Getting rid of indoor radon, Ilomantsi, Finland
Getting rid of indoor radon
Markku Savola's two-storey detached house was renovated, thanks to which the radon concentration in the indoor air was controlled and reduced. At worst, radon increases the risk of lung cancer.
Faits sur le projet
- We are satisfied with the radon repair and the work of the contractors. The radon concentration in the downstairs room was as high as 1,188 becquerels before the radon renovation, but dropped to 83 after the radon system was installed. A similar decline was also seen upstairs, where radon values fell from 621 becquerels to 20, Savola says.
Savola had long been planning the project because he knew the health risks of radon-containing air. For example, the recommendations of the Radiation and Nuclear Safety Authority (STUK) state that in an old house, the concentration of radon in the indoor air exceeding the limit value of more than 200 becquerels gives cause for renovation. The reason is that when exposed to indoor air, radon is a health risk that increases the susceptibility to lung cancer.
Radon increases the risk of lung cancer
- Anyway, the health risks are close to my heart, because I worked as a doctor before I retired.
Radon, Rn, is an invisible, colorless and odorless radioactive gas present in the indoor air of buildings. It is considered to be the most significant cause of lung cancer indoors after smoking. As a result of radon, about 300 Finns get lung cancer every year.
Radon is especially present during the winter, when the indoor air is warmer than the air outside the house. The temperature difference causes a vacuum in the house, which absorbs radon from the soil into the indoor air along with other air.
- Radon increases the risk of lung cancer, but not other diseases. We don't smoke. If we got lung cancer, I think the reason would be clear: radon, Savola explains.
Markku Savola built his house with his family in 1986−1987, when there was little talk of radon. However, during the construction and design phase of the house, he studied radon maps in the area, which did not find any information about the elevated radon concentrations in the Ilomantsi area. The reason was the lack of measured values. Savolo's house is in the danger zone for radon, as it is located on a ridge landscape and on a slope. Radon is usually transported to the indoor air from the soil under and around the building. In coarse gravel, the currents become large and the coarse fillers promote the currents.
- The basement space on the slope side of the house is built in the ground. The soil is quite coarse gravel. The foundation is based on a foot and an earthen slab. The wall between the slope and the basement is concrete casting, Savola says.
Readings of Ilomantsi's highest
The Savolas made the first radon measurements as early as 1992, when the radon concentration rose to as much as 1,360 becquerels. After this, the seams of the bottom of the house were sealed as well as possible, as a result of which the radon concentration started to decrease, but not to a low enough level. Over the years, compaction work has continued, but concentrations have remained high.
Then in 2013, Savola made a decision on radon remediation, as the concentration in the ground floor rose alarmingly to over 2,000 Bq / m³. The readings were the highest in Ilomantsi if you compare them with other measurement results made during STUK's campaign. As a result, Savola participated in radon training organized by STUK and requested an offer from Uponor to carry out radon renovation. The contract was carried out by WP-Pipe, a HVAC company in Joensuu, which installed Uponor's radon system next to the slope-side wall. The system included plastic suction and transfer ducts, an exhaust fan installed in the fan well and a ventilation pile.
Quick and easy contract
The installation contract went quickly and easily in one working day. The work began with the excavation of a well of about three and a half meters. At the bottom of the well came crushed stone and a vacuum cleaner, from which came about a 15-meter drainage pipe.
An exhaust air fan built into the system creates a vacuum under the house, which absorbs radon gas into the suction duct and moves it out of the vicinity of the house in a controlled and safe manner along the exhaust duct.
- Previously, measurements were made over a two-month measurement period with equipment supplied by STUK. Just before and after the installation of the vacuum cleaner, the measurements were made with a Ramon 2.2 meter, which means that the measurement time was 2 days, Savola specifies.
- Uponor's radon removal system is a well-thought-out radon gas control solution. All installation accessories came with the radon renovation system, says Pekka Riikonen, CEO of WP-Pipe.
Renseignements sur le projet
Renseignements sur le projet
Weber Hill Villas
Maison des Twin Cities (villes jumelles)
Archetype Sustainable House
Putman County Home
mini-maison de luxe
Changjia Residential Villa in Kunshan (Suzhou), China
Sheshan yard Shanghai
Radon renovation – a one day job
Hot tap water delivered energy efficiently
Uponor's brand-new technology for a wavelike log house
Sustainable tourism requires action
Underfloor heating for single family home with Comfort E
Heating of House Beauty is controlled by Uponor Smatrix Pulse control system
At the housing fairs of Kouvola, in summer 2019, was presented House Beauty which has the modern control system Uponor Smatrix Pulse for radiant underfloor heating and cooling system.
Testing Underfloor Cooling in record high heat wave
Uponor's radiant underfloor heating and cooling system was installed in a new single family house. During the record high heat wave, the system was in real action.
Kapanen's dream home is a fine place to live
A pilot project that still works like a dream
The biological treatment plant is worth its price
Increased living comfort thanks to underfloor cooling in a single-family house in Oulu
The plumbing renovation of a single-family house was completed in less than two days
Renovation of the district heating piping system of six housing companies
Jugendstil Villa in Leipzig
Green Land in Amman, Jordan
Feng Shui home
Cottage in Tuscany
Requalification of suburban areas with energy efficient residential buildings
Uponor Self-attaching Panel for a country cottage in Tuscany
Spectacular living in a luxury townhouse
Uponor Pre-insulated pipe system in link-attached houses in Fittja, Stockholm
Uponor Ecoflex Thermo VIP installed in a summer house
Lower heat losses with pre-insulated pipes laid in LECA at Lillhamra, Sweden
Aberdeen City Council
Balliol College, Jowett Walk.
Blackmill Doors Windmill
Branksome Care Home
Dervus Modular Volumetric Systems
Changzhou Tian'an Villa is located in Wujin District of Changzhou City.
A gray water filter provides operational reliability and ecology for Lake Ruuhijärvi
At the end of autumn 2013, Uponor's new product, Uponor Gray Water Filter Home, was installed in Ruuhijärvi, Nastola.
The plumbing in order in a single day
The 30 years old copper plumbing of the house were replaced with a Uponor composite system. The renovation was over in one day. The contractor for the job was LVI-Dalton Ltd from Klaukkala, Finland.