Renovation of cast iron water supply pipeline - swagelining, Łódź, Poland
Renovation of cast iron water supply pipeline - swagelining
Dąbrowa water supply in Łódź pumps water from Water Treatment Station at Lodowa Street to Stoki Reservoirs at Pomorska Street. The water is accumulated there and then delivered to 1/3 of the city. With the help of the Cohesion Fund from the European Commission, in mid 2008 the city started a project called Water lines and sewage treatment unit in Łódź II. The total value of the works carried out under this project was EUR 142 million. The project also included the contract “Dąbrowa Water Line – modernisation of Łódź Water Supply System – Part 02C Dąbrowa Water Line – Modernisation of treated water line” with a value of almost EUR 3.5 million. The water line with a nominal diameter of 750 mm and approximately 5,440 m long, was modernised under this project.
The Employer (Łódzka Spółka Infrastrukturalna) suggested that the water line be renovated using swagelining technology. Swagelining is “a tight fit” method which concerns putting PE pipes of temporarily reduced diameters into the damaged pipeline (it takes place by heating the pipes and applying the constant drawing force). After the pipe is pulled the drawing force is released and PE pipe through expansion adapts its diameter to internal diameter of old pipe. This way additional structural reinforcement of repaired pipeline is obtained.
For this purpose the contractor Wiertmar initially used DN/OD 800 SDR17 PE pipes, with a wall thickness 47.4 mm, made by X. “We do not quote the manufacturer’s name on purpose since the test has not been successfully completed. The works were carried out in the winter. They started with butt-welding 12-metre pipe lengths. It turned out, however, that the X pipes were stiff, with low plasticity and they did not keep the round dimension”, said Mr Marek Piekarski, the Chairman of Wiertmar. “It was difficult to position them correctly in the welder.” Later, however, a yet more serious problem was identified. After the welding stage, the installation phase followed, during which the weld broke while the pipe was being pulled through the reducer. Therefore, the PE pipe was taken out immediately. Fortunately, the pipe had not relaxed and so was not tightly fitted into the original pipe.
The contractor decided to analyse this situation and sent the X pipes to two laboratories to be tested. On the basis of the test results it was concluded that the pipes did not meet the requirements of PN-EN 12201-2 standard in terms of wall thickness. The other test results met the requirements of the standard. It was decided to keep the X pipes, since extensive tests performed in adverse weather conditions indicated that it was possible. Unfortunately, this time too, the test failed and the weld broke.
Therefore, it was immediately decided to change the pipe manufacturer. This time WehoPipe PE100 DN/OD 800 SDR17 PN10 pipes, wall thickness 47.4 mm, produced by Uponor Infra (former KWH Pipe Poland), were chosen. On special order, 15-metre pipe lengths were manufactured to shorten the welding time. The pipes were delivered to site a few days later. “It was enough just to look at the pipe surface to see a considerable difference between the KWH and X pipes” said Marek Piekarski. “The pipes delivered kept their round shape, their surface was perfectly smooth while the X pipe surface resembled orange peel. We also noticed that the new pipes had higher plasticity.”
This time welding was smooth and fast, and installation went without any problem.The tight fit method was applied in the first section of the water supply pipeline at the exit from the Water Treatment Station, where the highest hydraulic hammering occurs and where the pipeline was used the most, near the passages under a very busy roads (Dąbrowskiego, Przybyszewskiego, Piłsudskiego streets), under PKP tracks and tram tracks.
The Łódź contract was another test both for the contractor, Wiertmar and for Uponor Infra, the pipe manufacturer and supplier. Although swagelining technology was a great challenge, thanks to this method it was possible to minimise inconvenience to traffic. Most of the work was carried out in the centre of a city with a population of 750,000, in a built-up area, along traffic lanes with heavy traffic of motor vehicles and trams, in adverse winter-spring conditions. The fact that Wiertmar is ready to continue using swagelining technology can be seen as a special acknowledgement of WehoPipe and Uponor Infra.
Parameters of renovated pipeline:
- outer diameter of the PE pipe used as the lining - 800 mm;
- inside diameter of renovated pipeline - 750 mm;
- outer diameter of PE pipe after it was pulled through the reducer – approx. 730 mm;
- outer diameter of PE pipe after relaxation process – approx.760 mm.
Consortium of companies: Infra SA (consortium leader), PBG SA (consortium partner), Wiertmar sp. z o.o. (consortium partner) and Bud-Inż. sp. z o.o. (consortium partner)
Uponor tryckrörssystem Profuse i Borås Stad
Storsatsning vid Skånes universitetssjukhus i Malmö
Testinstallation av infrakulvert med stor potential
Starkt, säkert och flexibelt
Innovativt - Pålitligt - och installerad på 11 dagar
Uponor markavloppssystem Ultra Rib 2 i Kungälv
Säkert och Hållbart
Fokus på framtida hållbarhet
Weholite installerat i Valdemarsvik
Uponor Vault renar dagvatten
ProFuse installerat i Borås Stad
Första installationen av Ultra Rib 2 Blue
Plastic ensures condensation-free ventilation at new hospital and research facility
Pump structure secures stormwater system’s long life
Drinking water passing through contaminated area in Thisted
Intake pipeline for seawater in Copenhagen Harbour
Butt welding by night of 900 mm pipes ensures stable operation of a district cooling solution in Copenhagen Harbour.
Heavy-duty pipe for Tallinn’s district heating network
PE pressure sewer system from Harjavalta to the city of Pori
New Uponor IQ –Storm water system - Sustainability and Quality in Road Infrastructure
Ultra Double replace concrete pipe line in Raahe
ProFuse pressure pipe line provides drinking water to cottage owners in islands near by Uusikaupunki
Environmental friendly heating and storm water systems in new Launonen day-care centre
New water pipeline
Now that’s truly FAST
Secure tunnel trunk lines
Handling storm water in a smart way
Life is grand for graylings in the pure waters of Ounasjoki River
Europe’s largest ever plastic culvert goes to Norway
Don’t count on luck to protect you from flooding
Urban runoff under control – quickly and easily
Relining to the rescue in Kajaani
Clean drinking water for 17,000 scouts
Iisalmen Vesi renovated a trunk line by relining
To rebuild an office building located in the heart of Amsterdam into 150 appartments in a relatively short time is definitely a big challenge.
Weholite limits overflows and pollution in London
Fighting against an ecological disaster in a world-record time
Rapid action was critical when a sewage collector broke in Warsaw, Poland, causing a massive waste spill into the Vistula River. Uponor Infra’s crew worked 24 hours a day in order to stop the pollution of the river. A temporary pipeline was produced, delivered and connected in just eight days.
Sewage pipelines to sewage treatment plant - HDD method
Collectors for sewage treatment plant
Renovation of reinforced concrete sewer - relining method
Sewage retention chanel
Sea outlet - discharge of stream water into the Gdańsk Bay part 2
Renovation of damaged stoneware collector – cracking/short relining
Sewage separation system
Construction of storm water collectors in Nowe Polkowice is one of the stages of a big investment concerning the drainage of the district.
Sea outlet of treated wastewater
A sea outlet of treated wastewater was initiated in Swarzewo. It is yet another of the many environmentally friendly projects that have recently been carried out in Poland where PE pipes were used.
Hybrid solutions for storm water management
City of Lahti is building new neighborhood called Ranta-Kartano. While they were constructing basic infrastucture the city saw the possibilty to reserve some ground space for storm water management. Now there is a test running for different kind of storm water management. Uponor is involved with new type of storm water filter.
An easy and reliable storm water solution
Flow measurement reveals leaks in the water supply network
Fire wastewater safely recovered
Water treatment plant
Quick installation in the Konotopa channel
Weholite tanks have multiple uses
Water supply in very demanding terrain in Norway
A smart retention system for an anti-flooding solution
September 2018 saw the launch of the project for a stormwater drainage system in Rzeszów, almost 26 kilometres long, in the residential District of Budziwój, which partially coincides with the floodplain of the River Wisłok. One of the elements of this system is the retention canal. The project, scheduled for delivery by May 2020, will help to finally solve flooding problems which have been plaguing the residents of this region of Poland.